Some parts of this roof were not installed properly. In this photo, you can see there was no underlayment or felt installed before shingles.
In this photo, you can see where a tree limb struck and damaged shingles. This is likely to be leaking or cause a leak in the near future
The boot on the left side in this photo appears to need to be serviced.
There are some pitting and signs of wear on all of these shingles. This could be due to a lack of ventilation and the age of the shingles.
The gutters are not in great shape. In this photo, you can see that the gutter and facia are damaged and pulling away from the rafter tails.
Visual Marketing By Lead Symphony – Patent Pending